Top-Flight AC Repair & HVAC Services For Franklinton, NC
Bust out your capes and masks, folks! Heroes Heating & Cooling are here to save the day in Franklinton, NC. As HVAC superheroes, we take our mission very seriously - protecting the comfort of all our customers, one AC repair at a time! But we don't stop there. Our services extend beyond just repairs; we also offer top-notch HVAC service, indoor air quality services, and commercial HVAC expertise. Our team of trained professionals is dedicated to making sure each and every customer is comfortable and satisfied. So don't wait! Call on Heroes Heating & Cooling today and let us save your day!
Our Fans In Franklinton, NC Are Singing Our Praises!
Calling all citizens in need of exceptional service - we understand that choosing a heating and cooling company can be a daunting task. But fear not, Heroes Heating & Cooling is here to save the day! Our best advertisements are the words of our loyal customers and we are thrilled to share their glowing reviews with you. Our team of HVAC professionals takes pride in providing top-notch service, and our customer feedback speaks volumes. Check out our reviews below to read firsthand accounts of our heroic work. And when the time comes for your own HVAC distress signal, give us a call at 919-632-0402 or message us online and experience the power of Heroes Heating & Cooling for yourself.
for Franklinton, NC
Our Reviews by City
Arrived due to continued issues with first floor American Standard AV/Furnace. System was installed in 2019. Corrected wiring from installation of condensate removal pump to allow proper shut off of the system incase of condensation back up. Nest thermostat was still giving error message of issue with Y wire. Further diagnostic revealed a failed voltage distribution system. Component attracted ants due to heat it emits during operation. Build up of ants caused component to short out and fail. Informed homeowners of findings and discussed repair options. Homeowner elected to proceed with repair of the failed component. Removed failed voltage distribution system and installed new voltage distribution system. Tested system operation, system is operating within manufacturer specifications at this time. Thank you for choosing Heroes Heating and Cooling and allowing us to save the day!
After a thorough inspection, i seen that everything is in excellent condition. The blower amps, flame sensor, capacitor, and contactor all checked out perfectly. Also ensured the smooth transition of the A/C to Heat mode, and everything is running just fine.
Found system air conditioning rheem outdoor unit not running upon arrival. Upon further inspection found bad dual start assembly. Also found out door air conditioning coil dirty. Replaced dual start assembly. Will return tomorrow to clean outdoor coil
Returned 08/21/23 to replace heat transfer coil. Recovered refrigerant then removed leaking heat transfer coil. Installed new coil then pulled vacuum to 500 microns. I then recharged the system to manufacturer’s specifications then tested system operation. System is operating properly at time of departure. Thank you for choosing Heroes Heating and Cooling!
Cleared drain line. Needs condensate pump installed on first floor heat pump.
Found system low on charge upstairs. Customer indoor coil is leaking. Also found contactor pitted. Will return to replace coil and contactor. Also checked downstairs system. Found system compressor going bad. Also found downstairs dual start assembly weak. Found downstairs contactor pitted. Will find out if system is under warranty and follow up tomorrow