Saving The Day With Superior HVAC Services For Zebulon NC
Welcome to Heroes Heating & Cooling, your one-stop-shop for all HVAC needs in Zebulon NC! Whether temperatures are soaring or plummeting, fear not – our team of HVAC superheroes is here to save the day. We offer a range of services to keep your home comfy and cozy, delivered with unparalleled professionalism and superhuman expertise! First, our air conditioning repair, installation and maintenance services are second to none! No matter how tricky a problem you’ve got, our super-powered technicians can handle it. But wait, there’s more! When winter’s chill descends upon us, our heating repair, installation and maintenance services come to the rescue! Our heating mastery will keep you snug and warm even through the iciest months. Plus, let’s not forget HVAC’s sidekick – indoor air quality! Our IAQ services do battle against all the dust, allergens and indoor pollutants that threaten your home. But what truly sets us apart is our team. Our superheroes are expert, friendly technicians with a passion for their craft and a commitment to swift, excellent service. So Zebulon citizens, never fear HVAC troubles again! Trust Heroes Heating & Cooling to swoop in and save the day!
So if you’re in search of the ultimate HVAC heroes to rescue you from the clutches of discomfort, you’ve found them – but don’t just take our word for it. Hear it straight from your neighbors in Zebulon NC. Our review pages are treasures troves of tales of satisfied customers regaling you with epic encounters with our top-notch service. Discover how we defeated faulty ACs, conquered malfunctioning furnaces and triumphed over indoor air quality villains! Then, when you’re ready to unleash the power of unbeatable comfort, send us a message online or give us a call at 919-632-0402 – we’ll be on the way!
for Zebulon, NC
Our Reviews by City
Here a fall maintenance performed on a furnace, and biological growth found in the supply plenum. A uv light is recommended to stop growth from getting worse. Also dust is starting to build up in the return plenum, and that warrants a Brett filter system to keep the system clean. All amp draws are within tolerance, and are as follows indoor fan 3.71 amps combustion fan .99 flame sensor at 7.1 mili volts igniter at 56.2 ohms the single start assembly is giving what it’s rated for at 5.0 uf, and the heat rise is at 33* which is within manufacturing specifications. The system is running in heat as of now.
Replaced indoor coil.
Here a two system fall maintenance performed, and no mechanical issues to report. The upstairs amp draws are as follows indoor fan .75 amps heat strips are working properly compressor 4.08 outdoor fan .46 the dual start assembly is giving what it’s rated for at 29.3/4.9uf suction pressure 135psi discharge at 375psi. Downstairs heat strips are working properly indoor fan amps .92 compressor 4.80 outdoor fan 1.09 suction pressure 110psi discharge 400psi dual start assembly giving 30/7.5uf. Both systems are running in heat efficiently. The home has excessive dust within, and a better filter is recommended along with air purification.
Arrived to perform heating maintenance. System is 2018 Lennox heat pump which services the whole home. Tested all heating components and heating operation. System is operating at manufacturer’s specifications at this time. Recommended air purification solutions due to build up of bacterial contamination inside of the system.
Found system compressor out. Gave customer options to make repairs. Customer declined options
Arrived to perform replacements of indoor heat transfer coil, dual start assembly, contactor, and install Honeywell Wi-Fi thermostat. Removed all old components and installed new components. Tested system operation. System is operating at manufacturer’s specifications at this time. Installed new thermostat and walked homeowner through on set up. Thank you for choosing Heroes Heating and Cooling and allowing us to Save The Day!