Saving The Day With Superior HVAC Services For Willow Spring NC
Welcome to Heroes Heating & Cooling, your one-stop-shop for all HVAC needs in Willow Spring NC! Whether temperatures are soaring or plummeting, fear not – our team of HVAC superheroes is here to save the day. We offer a range of services to keep your home comfy and cozy, delivered with unparalleled professionalism and superhuman expertise! First, our air conditioning repair, installation and maintenance services are second to none! No matter how tricky a problem you’ve got, our super-powered technicians can handle it. But wait, there’s more! When winter’s chill descends upon us, our heating repair, installation and maintenance services come to the rescue! Our heating mastery will keep you snug and warm even through the iciest months. Plus, let’s not forget HVAC’s sidekick – indoor air quality! Our IAQ services do battle against all the dust, allergens and indoor pollutants that threaten your home. But what truly sets us apart is our team. Our superheroes are expert, friendly technicians with a passion for their craft and a commitment to swift, excellent service. So Willow Spring citizens, never fear HVAC troubles again! Trust Heroes Heating & Cooling to swoop in and save the day!
So if you’re in search of the ultimate HVAC heroes to rescue you from the clutches of discomfort, you’ve found them – but don’t just take our word for it. Hear it straight from your neighbors in Willow Spring NC. Our review pages are treasures troves of tales of satisfied customers regaling you with epic encounters with our top-notch service. Discover how we defeated faulty ACs, conquered malfunctioning furnaces and triumphed over indoor air quality villains! Then, when you’re ready to unleash the power of unbeatable comfort, send us a message online or give us a call at 919-632-0402 – we’ll be on the way!
for Willow Spring, NC
Our Reviews by City
Found upstairs fuse blowed. Changed fused and wrapped up with tape so it won’t touch anything. System Is working normal
Found upstairs system low voltage fuse blowed. Replaced fuse and system is heating at this time. Did not find any reason for fuse to blow
York 15 seer heatpump system
Arrived due to homeowners concerns of mold inside duct work. System is 2002 Rheem heat pump with duct system original to the home as well. Performed inspection of the ducting system as well as the heat pump. Found the air handler and ducting severely contaminated with biological contamination as well as dirt and debris. The system would not operate in heat mode as the blower woukd only operate intermittently. Found the high voltage disconnect melted due to wiring issues with the air handler as several other severe issues within the system. Informed homeowner of findings with system and presented pictures supporting findings. Recommended system and duct system replacement due to the overall condition of the unit/ducting. Homeowner elected to meet with project manager to further discuss system retirement. Thank you for choosing Heroes Heating And Cooling!
Arrived due to no AC. System is 2014 Goodman heat pump which services the whole home. Upon arrival found indoor blower non operational. Diagnostic revealed a failed single start assembly. Component was recently replaced in July of this year. Installed new single start assembly to test motor operation. Blower began to run however the operating amperage is high. Informed Logan of findings and discussed repair options. Logan agreed to replace single start assembly for now. Repairs perform successfully, system is operating properly at this time. Thank you for choosing Heroes Heating And Cooling!
During their maintenance, I conducted a thorough assessment of two furnaces, one of which was a Carrier and the other a York model. Both furnaces were found to be in excellent condition, with their flame sensors functioning optimally. Notably, the Carrier furnace exhibited a Delta T of 17.2 degrees, while the York furnace had a Delta T of 19.7 degrees. Drain lines were clear, and all electrical components were in good shape. I recommended the installation of an SS2 switch for the Carrier unit, which the homeowner opted not to implement immediately but should consider for future maintenance. Following the furnace checks, I proceeded to inspect the condensing units. The refrigerant levels were within the normal range, and all electrical components of the condensing units were also in excellent condition. Overall, both furnaces and condensing units were in good shape, and necessary recommendations were provided for the homeowner's consideration.
Found upstairs system drain pan full of water. Customer has a clogged drain line. Also found upstairs contactor assembly pitted. Found downstairs breaker tripped. Restarted breaker and found downstairs compressor going bad. Also found upstairs system low on r22 charge. Customer has a leak in system. Gave customer options to make repairs. Customer only wants to clear drain line and pan and replace contactor assembly. Made repairs.
During service call, tech found a malfunctioning blower motor. Indoor coil will freeze if there is not proper airflow blowing over it. Tech found 240 volts going to blower motor but motor would not start. Tech recommends blower motor and fan relay board replacement to address issue. Unit is not functioning at this time.
Arrived to replace the second floor systems compressor. System is 2021 Coleman heat pump. Recovered refrigerant from system and removed old compressor. Installed then brazed in new compressor. Pressure tested the system then pulled system to 500 microns of vacuum to ensure all moisture and air is removed from the system. I then charged the system to manufactures specifications. System is operating properly at time of departure. I have requested another appointment to finish the remaining media filter installation. Returned installed both upstairs and downstairs media filters