Saving The Day With Superior HVAC Services For Bullock NC
Welcome to Heroes Heating & Cooling, your one-stop-shop for all HVAC needs in Bullock NC! Whether temperatures are soaring or plummeting, fear not – our team of HVAC superheroes is here to save the day. We offer a range of services to keep your home comfy and cozy, delivered with unparalleled professionalism and superhuman expertise! First, our air conditioning repair, installation and maintenance services are second to none! No matter how tricky a problem you’ve got, our super-powered technicians can handle it. But wait, there’s more! When winter’s chill descends upon us, our heating repair, installation and maintenance services come to the rescue! Our heating mastery will keep you snug and warm even through the iciest months. Plus, let’s not forget HVAC’s sidekick – indoor air quality! Our IAQ services do battle against all the dust, allergens and indoor pollutants that threaten your home. But what truly sets us apart is our team. Our superheroes are expert, friendly technicians with a passion for their craft and a commitment to swift, excellent service. So Bullock citizens, never fear HVAC troubles again! Trust Heroes Heating & Cooling to swoop in and save the day!
So if you’re in search of the ultimate HVAC heroes to rescue you from the clutches of discomfort, you’ve found them – but don’t just take our word for it. Hear it straight from your neighbors in Bullock NC. Our review pages are treasures troves of tales of satisfied customers regaling you with epic encounters with our top-notch service. Discover how we defeated faulty ACs, conquered malfunctioning furnaces and triumphed over indoor air quality villains! Then, when you’re ready to unleash the power of unbeatable comfort, send us a message online or give us a call at 919-632-0402 – we’ll be on the way!
for Bullock, NC
Our Reviews by City
Checked full system tune up. Checked duct work for growth and found dirty duct system. Checked safeties. Checked blower amps 2.68. Checked heater amps 39. Refrigerant pressures 425/125. Compressor amps 10.2. Outdoor fan amps .98. Found dirty duct system. Will return to clean and sanitize duct system. Also will install uv light.
Arrived due to no heat/ac. System is 2019 Coleman heat pump which services the whole house. Upon arrival found outdoor heat pump locked out due to high pressure fault. Reset power to the control board to test system. Found failed condenser fan motor/module on system start up. Will have to replace failed components for proper system operation. Thank you for choosing Heroes Heating And Cooling. Returned 10/30 to replace condenser fan motor and module. Removed failed components and installed new motor and module. Tested system operation. System is operating properly at this time. Also instructed homeowners on how to use thermostat.
Preformed full system tune up on Coleman heat pump spit hvac system
Will come back Monday to do tune up